Two xxx hp domestic water booster pumps supply the necessary water pressure for the buildings. These pumps are designed to supply up to xxx ft.wc. of additional head at a flow rate of xxx usgpm
Pressure reducing valves (PRVs) at the outlet of the pumps substantially reduce the pressure, so that only about xxx ft.wc. is actually added.
The pressure drop across the PRV’s results in a significant drop in efficiency.
We recommend installing variable speed drives and inverter duty motors on the two booster pumps. Any PRV’s on the main line leading to the penthouse should be opened completely or entirely removed to reduce the system losses.
We recommend installing a pressure sensor on the piping in the penthouse, and controlling the VSD’s to maintain a certain pressure (say 20 psig).